What are the general faults of the air shower room? How to deal with the failure of air shower room? Next by our country professional high-end air shower room manufacturing expert for you to answer this question:
First, the power switch. Usually the air shower room has these places to cut off the power supply:
1. The power switch of the box outside the air shower;
2, the air shower box control panel;
3, on both sides of the air shower box (here the power switch can prevent the emergency cut off the power supply, effectively improve the personal safety of the staff). When the power indicator is blocked, you may wish to check the air shower power supply.
Two, the air shower fan does not work. When the air shower room does not work, it is time to check whether the emergency switch of the outdoor cabinet of the air shower is cut off. If it is cut off, gently press with your hand and rotate to the right to let go.
Three, the air shower fan inverted or the wind speed is very small, please be sure to check whether the 380V three-phase four-wire line reverse connection, general air shower manufacturer factory installation will have a special electrician connected line; If the line source of the air shower is reversed, the light will lead to the air shower fan does not work or reverse the wind speed of the shower room is reduced, the heavy will burn the circuit board of the whole air shower room; It is recommended that the use of air shower enterprises do not lightly to replace the wiring, because the production needs to determine to move, please consult the air shower manufacturers to solve.
Four, the air shower room does not blow, in addition to the above three points, also need to check whether the emergency stop key inside the air shower room is pressed, such as the emergency stop key for the color, the air shower room will not blow; To press the emergency stop button again can work normally.
Five, the air shower room can not automatically induction blowing, please check the air shower room box in the lower right corner of the light sensing system, to see whether the light sensing device is installed correctly, such as the two sides of the light is opposite and the light sense is normal, you can automatically induction blowing.
Six, the air shower room for a period of time when the wind speed is very low, please check the air shower room at the beginning, high efficiency filter is too much dust, if so, please replace the filter. (The primary effect filter of the air shower is generally replaced once within 1-6 months, and the high efficiency filter of the air shower is generally replaced once within 6-12 months)